This article recommends practical methods for achieving high, i.e., 15°F (8.3°C) or greater, chilled-water temperature differentials (Delta T s) in variable flow hydronic cooling systems. Once high chilled-water Delta T s are realized, more Btu’s (J/s) of cooling will be accomplished per gallon (liter) of chilled-water distributed ( Figure 1 ). Pressure losses and pumping energy will decline considerably in existing hydronic cooling systems and smaller pumps and piping may be installed in new hydronic cooling systems. Also, water chiller capacities will no longer be limited by maximum evaporator flow rates and chilled-water storage tanks will store many more tonhours (MJ) of cooling. This fundamental approach provides significant, enduring improvements in the performance of variable-flow hydronic cooling systems.
Disclaimer: The information provided within this publication / eBook/ content is for general informational purposes only. While we try to keep the information up-to-date and correct, there are no representations or warranties, express or implied, about the completeness, accuracy, reliability, suitability or availability with respect to the information, products, services, or related graphics contained in this publication / eBook/ content for any purpose. Any use of this information is at your own risk.